Top Rated Heating & AC Repair Services in Claremore, OK
If you are looking for reliable home heating and cooling services in Claremore, OK, Innovative Air Pros is ready to help you and your family. Our experienced team of HVAC professionals provide expert AC repair, HVAC installation and maintenance tune-up services to ensure your comfort. In addition, we provide indoor air quality services to ensure a safe and healthy environment inside your home or business.
Our goal is to ensure that your heating and air conditioning system works efficiently and reliably year-round. We make it easy for our customers, providing same day service and after hours service when needed - so you can get the job done quickly and get back to living worry-free!
Book your appointment today for an AC repair, furnace installation or HVAC tune-up today.
for Claremore, OK
Our Reviews by City
Excellent, efficient, professional service
Challey - Claremore, OK 74019
The team arrived and did a furnace and a/c unit install in a quick professional manner! Excellent experience, addressed all out questions, and returned out home air conditioning to better than normal standards.
Response from Innovative Air Pros:
Your kind words mean a lot to us. Thanks for the positive feedback.
Annual furnace maintenance on three 2008 Lennox systems. The heat exchangers are in great shape for their age and the systems are performing as they should here today. The blower motor capacitors are weak and need replaced. Also the upstairs units blower motor bearings are loose.
For this job, Customer states when the air conditioner runs it puts off a weird smell every No and again. Technician arrived to the smell not arriving at the moment. Technician checked a few more components to ensure proper operation. System is running great at this time. Technician made several options for duct cleanings and UV lights to help eliminate any Odors, Bacterias, Allergens, Airborne Viruses, As well as Black Substance growth that grow within the HVAC system
Preformed a residential real estate inspection on two Trane systems. Found both units low on refrigerant units need to be leak searched. Found the drip legs done incorrectly they should be at a change of elevation. Filters are extremely dirty and need to be changed. The units should plenums on the return to reduce stress on the blower motor and also increase air distribution across the home.
Preformed yearly air conditioning maintenance on two systems. Checked all capacitors contactors amperage’s and cleaned the system. Units are both cooling good at this time. Would highly recommend adding surge protectors to the systems to protect your investment from lightning surges and power related spikes.
Service call for a unit not keeping up. Technician found the main breaker tripped and the capacitor failed. Once the unit was up and going the system was very low on refrigerant. Made all the proper repairs and got our new customer on the friends and family club.
Installed a new Goodman coil on the downstairs system.
Service call where the system wasn’t keeping up. Technician found a leak in the coil and the system low on refrigerant. We will be back out Monday to replace the coil.
Service, Technician installed new Power Humidifier, Installed new Humidistat above the filter base in the return, Installed New Inducer draft motor, Installed Blower motor capacitor, Installed New HSI Igniter, Tested the Humidifier it fired up and ran, Got it Set to 40% humidity right can be adjusted by the humidistat, System runs Great at this time.
Two System Furnace Tune Up, Checked all Capacitors, Checked and Adjusted gas Manifold pressures, Propane systems, Checked static pressures, Checked blower motor bearings, Checked Delta Ts, Checked and cleaned flame sensors, Checked and Changed all filters, Filter sizes- 2 10x20x1 and 1 12x24x1, Checked inducer motor amp draw, Checked blower motor amp draw, Checked both igniters for white or cracked spots signs of deteriorating, Checked both Heat exchangers for cracks, rust or major stress points, Customer already has two air scrubber, Technician found the system for the Bedroom side or backside of the cabin the Inducer motor is overamping which means it’s starting to pull to much power then needed the windings are starting to get hot meaning the Inducer motor is on a downhill slope, the Hot Surface igniter is looking pretty rough has severe white marks and deteriorating spots, as well as the blower motor capacitor is getting weak, Technician made options for repairs as well as made an
Service call, Technicians installed Two Brand new Air scrubbers with Ozone to eliminate all bacteria, Allergens, Black substance, and virus’s that grow thru out the HVAC Equipment, As well as signed up for a Pro club, Got all them installed Up and glowing.
Service call No Cool, System has a clogged and backed up drain in Claremore OK
Ac repair Claremore
Air conditioning service in Clare more