Unparalleled HVAC Service For Your Catoosa, OK Home
Innovative Air Pros is the name locals trust for HVAC service and maintenance in Catoosa, OK. With the best HVAC technicians in Oklahoma on staff, this experienced team offers speedy, quality HVAC work - whether you need AC repair and installation, furnace repair and replacement or special services such as heat pump repair or duct sealing. Innovative Air Pros also has extensive experience when it comes to improving indoor air quality with a variety of methods such as air filters, UV germicidal lights and air quality testing. You can rest assured that when you contact Innovative Air Pros for HVAC help, you're always getting the best in reliable services! See what your neighbors have to say about our work below!
for Catoosa, OK
Our Reviews by City
Two system tune up on a single residence home. A 4 year old Trane and a brand new American standard system. Both systems are operating as they should and mechanically solid. The Trane system is a little low on refrigerant and appears to be low from the initial install date.
Technician arrived to the system freezing up. Technician checked all the fittings and made sure there was no leaks. Technician checked refrigerant charge on the unit and was very low. Technician recommended to put 1lb of refrigerant in the unit to get it from freezing up. Everything is working properly at this time.
Two System A/C Maintenance Tune Up on Two 6 year old Carrier systems. Technician checked all safety devices and components that are in use during the A/C Season. Technician found the upstairs systems compressor is pulling a little high amp draw on start up but not over the max. Technician offered surge protectors for all pieces of equipment as well as a Hard start kit to help the high amp draw on the upstairs. Changed all filters, Filter sizes- 3 14x24x1.Systems work great at this time.
15.2 SEER2 AC and Single Stage Heater, Installed New full A/C System, Installed New Media Filter Base, Filter size- 20x20x5, Reconnected to existing copper lines, High Voltage, Low voltage, Supply and Return Plenums, Ran A New Condensate drain, Installed New UV Air Purification bulbs for the New Full system as well as the Other Existing Unit. Used Existing Thermostat, Sealed up any air leaks, System runs great at this time.
Arrived and leak searched the system. Found the leak in the evaporator coil of the air handler unit is from 2006 and runs on r22 refrigerant.
Service call for no heat but the system is working fine here today.
Service call, Technicians replaced control board, System works great. Technicians replaced gas valve last week.
Service call No Heat, Technicians found System has a bad gas valve, when glowing to ignite, The control board tells the gas valve to come on and it doesn’t it’s seized up, Replaced gas valve system works great at this time.
Found bad hot surface igniter. Replaced with a new OEM HSI igniter and insured proper operation.
Service call No Cool in Catoosa.
Air conditioning service in Catoosa
Ac repair Catoosa
Air conditioner repair Catoosa
Install blower motor in Catoosa.
Service call vents were smoking in Catoosa
Service call on Mazzios in Catoosa lobby unit isn’t running.